G2 I/O Remote
Controls station devices based on specific events or time of day and enables the monitoring and signaling of gates, doors, etc
The G2 IO Remote interfaces between the ATX Station Controller and field devices at the fire station. The inputs (I) can be configured to monitor switches such as doorbells, walk-in alert triggers and door open sensors. The outputs (O) can be used to signal automatic doors and gates, activate strobe lights and more.
The G2 I/O Remote may be installed up to 300 feet from the ATX Station Controller. Like all G2 peripheral devices, the G2 I/O Remote receives power and data via a single Ethernet CAT5 or CAT6 cable. The extruded, all-aluminum enclosure features laser-etched labels for all inputs and outputs. It has flanged end plates for easy installation.
Input and output rules are easily configured in the G2 Station Controller Interface. This enables individual outputs to respond to unit alarms, time of day alarms, and many more options. Inputs can be set to trigger other outputs, act as doorbell inputs, acknowledge calls and more.
US Digital Designs’ I/O rule software interface allows you to configure the inputs and outputs in an almost limitless fashion
Dimensions (W x H x D):
6.5 x 6 x 2 (in); 165 x 152 x 52 (mm)
(8) Dry contact
(8) Form A relays rated .5A @ 48V AC or resistive load only
(1) Ethernet/POE to Station Controller peripheral network
Indicators and controls:
Input and output active LEDs
USDD POE; optional 12 VDC input
A brief overview of the Phoenix G2 I/O Remote.
Want to streamline?
The new stand-alone Phoenix G2 Message Sign requires no additional power from the Sign Remote or Message Remote.
It’s easy to install: just plug in the Power over Ethernet (PoE) cable.